There are specific site and rack requirements for the SD-WAN 4000/4100/5100 SE appliances. You must make sure that adequate environmental control and power density are available. Racks must be bolted to the ground, have sufficient airflow, and have adequate power and network connections. Preparing the site and rack are important steps in the installation process and help ensure a smooth installation.
should be installed in a server room or server cabinet with the following
conditioner, preferably a dedicated computer room air conditioner (CRAC),
capable of maintaining the cabinet or server room at a temperature of no more
than 27 degrees C/80.6 degrees F at altitudes of up to 2100 m/7000 ft, or 18
degrees C/64.4 degrees F at higher altitudes, a humidity level no greater than
45 percent, and a dust-free environment.
- Power density
capable of handling at least 4,000 watts per rack unit in addition to power
needs for the CRAC.
The rack on which you install your appliance should meet the following criteria:
- Rack characteristics
- Racks should be either integrated into a purpose-designed server cabinet or be the floor-to-ceiling type, bolted down at both top and bottom to ensure stability. If you have a cabinet, it should be installed perpendicular to a load-bearing wall for stability and sufficient airflow. If you have a server room, your racks should be installed in rows spaced at least 1 meter/3 feet apart for sufficient airflow. Your rack must allow your IT personnel unfettered access to the front and back of each server and to all power and network connections.
- Power connections
- At minimum, two standard power outlets per unit.
- Network connections
- At minimum, Ethernet connection per rack unit.
- Space requirements
- Two empty rack units for SD-WAN 4000/4100/5100 SE appliances.